Wood burning boiler stove with two doors and ceramic tiles.
Color : black
- Not to be fired when not connected to radiators / fan convector heaters. Burning wood in the fireplace without water in the boiler will cause it to crack and subsequent loss of the guaranty.
Achieving the desired heat output depends on:
- We recommend the installation to be done in an open type system.When connected in closed circuit system it must be fully protected using safety valves for temperature and pressure up to 1.5bar. All elements of the installation must be protected from freezing. In installation with forced ciculation we recommend the pump to be backed-up by a UPS.
- In case of presence of copper in any part of the plumbing installation the fireplace must be protected from electrolysis by installing a magnesium anode or other protective system.
|Country of Manufacture||Bulgaria|
|Heat output (kW)||15|
|Space heating output (kW)||5|
|Water heating output (kW)||10|
|Maximal thermal output (kW / BTU)||15 / 51182|
|Heating type||Hydro - Radiator|
|Nominal thermal power (kW)||10|
|Approximate heating surface (m²/ft²)||75 / 807|
|Approximate heating capacity (m³)||202|
|Dimension Depth (mm)||545|
|Dimension Width (mm)||585|
|Dimension Height (mm)||985|
|Boiler capacity (L)||16|
|Combustion chamber dimensions (Height, Width, Depth), mm||415x385x350|
|Operating pressure (bar)||1|
|Fuel Type||Wood, Briquettes|
|CO measured at 13% Oxygen at rated power(reduced) [%]||0.0998%|
|Exhaust Location||Top side|
|Cold water inlet||1"|
|Hot water outlet||1"|
|Ship Bundle Items||Together|